You inspire... we materialize®
Basin Electric, a lignite coal-fired power plant in the upper Midwest, utilizes carbon steel Ortner rapid discharge railcars to transport coal to storage bunkers. Plant personnel were charged with finding a way to haul greater volumes of coal with the same number of cars to take advantage of the cars full storage capacity.
TIVAR® 88-2 LINERS IMPROVE BOTTOM DUMP RAILCAR OPERATING EFFICIENCY
|Application:||Ortner Rapid Discharge Railcars|
|Liner:||TIVAR® 88-2, 3/8” Thick|
|Bulk Material:||Lignite Coal|
|Problem:||Flow problems, sticking and freezing|
|Date Installed:||1997 & 1999|
Carryback was a major problem, particularly during the winter months. At one point, each car was accumulating 50 tons of carryback. Turnaround times at the raildump receiving bunkers had reached an unacceptable level. In addition, the power company was forced to use car shakers to discharge loads, damaging the railcars in the process.
The plant first opted to try TIVAR® 88-2 linings on the sloping end walls of 50 hopper cars. Although coal discharge improved notably, during the winter months, 2-3 tons of material would accumulate on the cross beams each trip, and with a standard two-trips-per-day schedule, build-up remained costly. Next, the utility designated two bottom dump railcars to test complete lining systems. Quadrant Engineering Plastic Products SystemTIVAR® team designed linings for the discharge doors and structural support components, including cross beams and center sills. Using thermoforming and proprietary welding techniques, the Quadrant Engineering Plastic Products team pre-fabricated linings using 3/8” TIVAR® 88-2 UV-resistant material. A certified SystemTIVAR® installation contractor installed one railcar lining each day.
Tested in year-round weather conditions, the 100-ton capacity cars showed less than 1/16-ton carryback - an insignificant amount as deemed by the utility. Turnaround times at the raildump receiving bunkers have been cut by as much as 50% and loads are effectively discharged without the frequent use of car shakers, thawing sheds or other techniques that fatigue railcar structures.
Due to the success of the test cars and savings through maximizing hauling capacity and shortened turnaround times, the power plant has fully lined all 50 railcars. According to power plant personnel estimates, the cost of the TIVAR® 88-2 liners was recovered in less than two years with a projected 8- to 10-year wearlife for the lining systems.
Important: Most plastics will ignite and sustain flame under certain conditions. Caution is urged where any material may be exposed to open flame or heat generating equipment. Use Material Safety Data Sheets to determine auto-ignition and flashpoint temperatures of material or consult Quadrant Engineering Plastic Products. WARRANTY: Characteristics and applications for products are shown for information only and should not be viewed as recommendations for use or fitness for any particular purpose. TIVAR® and SystemTIVAR® are registered trademarks of Quadrant Engineering Plastic Products, Inc.
Drop-in TIVAR® 88-2 liners solve coal bunker flow problems at coke plant.Open
TIVAR® 88-2 liners improve bottom dump railcar operating efficiency.Open
TIVAR® railcar end wall liners enhance aggregate flow and reduce costs.Open
Major cement plant solves limestone flow problem with TIVAR® 88.Open
TIVAR® 88-2 liners eliminate flyash build-up in wet precipitator system.Open
2007-2014 © the Quadrant group of companies. All rights reserved.